- Reviews (0)
Sixteen style B (Class B) initiating device circuits (IDCs).
All zones accept two-wire smoke detectors and any normally open contact devices.
Zones 1-16 configured as general alarm zones.
All circuits are power-limited and supervised, meeting the latest ULC requirements using fuseless technology.
Two built-in, style Y (Class B) Notification Appliance (signal) circuits (NACs).
NACs may be programmed: silenceable, Non-silenceable, Auto-silence
1.25 amps of NAC power, 3.00 amps of total system power.
Alarm, trouble and supervisory, relay output, 24volt operation.
Resettable four-wire smoke detector power @ 500mA. Non-resettable power @ 500mA
Integral battery charger capable of charging up to 18AH batteries (batteries over 4AH)
Require use of the external battery backbox or ULC listed equivalent).
Disable/enable control per IDC
Reverse polarity protection.